Chilled water flow rate guidelines for process chiller systems
Below are some simple chiller pipe sizing guidelines along with some basic tips on how to properly size and run you water lines to your chilled water process. Look over the chiller links they will greatly help if you need further information about chillers.
Pipe sizing guide based on 10' Head loss/100' of pipe (Old steel pipe C = 100 )
|1/2" = 2 GPM||1-1/2" = 30 GPM||4" = 320 GPM|
|3/4" = 5 GPM||2" = 50 GPM||5" = 600 GPM|
|1" = 10 GPM||2-1/2" = 90 GPM||6" = 900 GPM|
|1-1/4" = 20 GPM||3" = 160 GPM||8" = 2000 GPM|
These figures are based on a 100 ft run in steel pipe. In most cases the flow rates will be better.
Chiller Warranty Service- Click here for details
Professional Refrigeration Troubleshooter
The first hands on Chiller/HVAC/R troubleshooting handbook is out in publication. This is a must have book for you and your service technicians. It will save you time and money along with passing on the vast knowledge of 60 years experience.
Flow meters of all kinds...click here.......
Flowmeterdirectory.com is the most comprehensive web portal on flow meter technology, manufacturers, suppliers, and system designers. The site contains both commercial and non-commercial information on flow meter types, manufacturers, suppliers, articles and technology.
Plumbing sizes (chiller water systems 35-70F)
Rule of thumb tips for sizing:
|1. If ever in question, use the water line sizes exiting the chiller. The lines are that size for a reason. (Do not reduce)|
|2. Reducing lines will drastically reduce your heat removal from your process and increase your electrical running costs.|
|3. Install full port valves (ball style not gate valves). Make sure there are valves to isolate: screens, chillers, tanks and pumps.|
|4. Never use iron or steel piping. (always use SCH80 PVC, copper or stainless steel). SCH 80 is the least expensive & best.|
How to pick your water line sizes.
This page was last updated on January 3, 2016
Click on any of the below hyper linked topics- especially if your browser does not support the java navigation bar above.
Chiller technical support for, plastics chillers, printing chillers, oem chillers, MRI chillers, laser chillers, air dryers,, hvac chillers
Chiller sales for,, chiller rental, used process chillers 2-20 ton, used process chillers 25-80 ton, used chillers 90-350 ton, rental chiller 8-80 ton, rental chiler 100-400 tons
About John C Schaub Inc,, chiller service, rates and hours, geographic chiller service regions, customer references
What is a chiller, chiller refrigeration cycle, chiller tonnage equations, chiller tonnage design parameters, size a chiller, chiller sizing
Chiller antifreeze info,, dowtherm, dowfrost, freezepoint mixture, chiller phone support, chiller water treatment, chiller water flow rates, emergency chiller service
This site was created and maintained by Jack Schaub
|Any inquiries please E-mail the Webmaster: firstname.lastname@example.org|
|John C. Schaub Inc. (On line-11/96) 23 Adams St. Mt. laurel NJ. 08054 phone 856-235-2120|